When thinking about lighting, one of the forgotten areas is emergency lighting testing and maintenance. Typically, that’s because the emergency lighting for a building is sat there in the background, unused, often ignored and despite that it is frequently assumed that the emergency lighting will always work when required. That’s dangerous thinking.
We wouldn’t want our clients to find out the hard way that the emergency lighting system they had installed all those years ago won’t work when they need it most.
As well as full design and installation of emergency lighting , IO Power provide annual inspection, testing and maintenance as well as certification of emergency lighting systems.
- All of our electrical engineers are fully qualified and experienced in the testing of emergency lighting.
- IO Power are able to carry out 12 month statutory tests on your emergency lighting systems, ensuring that you are fully comply with your insurance and BS EN 50172:2004 / BS5266-8:2004.
- We can also supply standard or bespoke log books, so that following the full annual test, a designated member of your staff can quickly and easily perform monthly checks using an easy to follow (tick box style) log book and instructions.
Our lighting inspection and testing procedures include the following:
- Luminaire duration testing
- Cleaning of diffusers
- Battery charging functional check
- Supply of test results and/or log books
- Advice on any improvements required to meet current standards
Testing Emergency Lighting
Daily emergency lighting inspection (only for central back-up systems)
This check only applies to emergency lighting systems with one central back-up battery system. In this case, there is a daily visual inspection of indicators on the central power supply to identify that the system is operational. No test of operation is required. This test does not apply to emergency lighting with self-contained back-up batteries in each unit (standard emergency lighting).
Monthly Emergency Lighting Tests (This test can be conducted by the responsible person or a qualified electrician)
All emergency lighting systems must be tested monthly as part of your emergency lighting testing and maintenance schedule. The test is a short functional test in accordance with BS EN 50172:2004 / BS 5266-8:2004.
The period of simulated failure should be sufficient for the purpose of this test while minimising damage to the system components, e.g. lamps. During this period, all luminaires and signs shall be checked to ensure that they are present, clean and functioning correctly.
Annually (We strongly recommend that the annual test be conducted by IO Power as fully qualified electricians)
Updates to standards and Ongoing Training
All of our electricians will have been trained to the latest standards which reflect any changes that the update has brought.
BS 5266-1:2005 the standard for emergency lighting has been revised and is now entitled: BS 5266-1:2011 Emergency lighting – Code of practice for the emergency escape lighting of premises.
- Clearer guidance on the requirements for escape route emergency lighting luminaries and signs in different types of premises;
- Guidance including illustrations on the emergency lighting requirements for different types and sizes of rooms;
- Guidance on the requirements where sudden loss of an individual normal lamp could prejudice safety;
- Clearer guidance on the types of wiring systems and test facilities required for emergency lighting;
- Updated guidance on the appropriate emergency lighting systems for different premises;
- New improved certification including a ‘small’ system certificate;
- Guidance on the evaluation of existing premises to decide if the emergency lighting system is adequate for its current use.
For peace of mind use IO Power who are NICEIC approved contractors for your installation and annual emergency lighting testing and maintenance.
Please contact the office on 0333 577 0290